Even though pressure transducers today are more rugged and reliable than every before, pressure transducer installations occasionally fail.
Fortunately, it is easy for technicians to perform simple troubleshooting techniques to determine if the transducer is operational, regardless of whether it's a 3-wire voltage output, 4-wire voltage output, or a 4-20 mA loop transmitter.
Section 1: Troubleshooting assumptions
Section 2: 3-wire removed from pipeline
Section 3: 3-wire connected to pipeline
Section 4: 4-wire removed from pipeline
Section 5: 4-wire connected to pipeline
Section 6: 4-20 mA removed from pipeline
Section 7: 4-20 mA connected to pipeline
Section 8: Customer application stories
Fill out the form to the right to download the whitepaper. If you would like to speak with one of our Application Engineers, please call 800-257-3872.